Ritu Bollard
ID : 26951
Input power : 9W LED
Technical Description
K-Lite Bollard luminaire designed for surface mounted. Symmetrical light distribution. Luminaire made of extruded aluminium alloy (grade 6063) with pressure die-cast aluminium components of high corrosion resistance and external non corrosive stainless steel fasteners. Translucent polycarbonate diffuser. Pressure die cast aluminium mounting plate 129mm x 124mm x 4mm thick with 3 elongated holes 15 x 10 to suit M8 bolts at PCD 70 with pure polyester powder coating. This mounting plate along with foundation bolts of suitable size to be used for ensuring firm grouting into the specially designed foundation. Protection class IP65. Mechanical resistance IK08. Pure polyester powder coated RAL 9004 Black / RAL 9007 Grey aluminium / RAL 7016 Anthracite grey / Graphite grey. Available colour temperature 2700K / 3000K / 4000K / 6500K. Colour rendering index (CRI)90. K-Lite LED module with expected service life of at least 60,000 operating hours. Prewired with LED driver and suitable for operating on 240V, 50Hz single phase ac supply. Driver efficiency >80%, Power factor >0.90, THD <10%, Surge protection 3KV. Luminaire dimension : 130mm triangle x 800mm height. CE & BIS Certified. Inhouse NABL accredited lab.